BASIC FACILITY REQUIREMENTS
The following facility services are required at the machine area for
a) – Electrical Power
b) – Exhaust Connections
c) – Nitrogen Supply
d) – Compressed Air
SITE PREPARATION CHECKLIST
____ Electrical power provided for the machine as stated on your
company’s purchase Order ?
____ Properly rated circuit breaker or fused disconnect installed for the
____ Nitrogen source (if N2 Oven) correctly sized, located and plumbed to
the oven location ?
____ Compressed air supply correctly sized, located and plumbed to the
oven location ?
____ Exhaust correctly sized and located?
THE WORK ENVIRONMENT
The machine will operate most effectively in a properly conditioned
environment. Excessive heat, cold, drafts, dryness, humidity, shock,
vibration or dirt may adversely http://propeciafinasteridestore.com affect the operation of the machine.
The system is designed to operate within the following environmental
Temperature: 55o – 90o F (13o – 32o. C)
Humidity: 20% – 90% NON-CONDENSING
Installation should be on a vibration-free floor surface. The
recommended surface is a properly treated concrete floor with
sufficient structural rigidity to eliminate the transmission of vibration to
the machine. The floor should have the strength to support the weight
of the machine and permit proper leveling of the machine. Concrete
floors should be treated for dust prevention.
The lighting level should be adequate in the work area around the
machine to allow operation, servicing and maintenance without glare
Write a Comment